How to wire a Pyronix Delta bell to Texecom Elite 48 Panel
Grade 3 wiring of Pyronix Delta bell to Texecom Elite 48 panel
All grade 3 wiring should have a fault circuit and it should be monitored 24 hours. The below diagram explains how to wire a grade 3 Pyronix Delta bell to a Texecom Elite 48 panel.
- The SAB should be powered with panel SAB connections and loop the tamper return. This will deploy a tamper circuit for the SAB.
- Strobe should be wired to the strobe terminal.
- Sounder should be wired to the sounder terminal.
- Fault or Aux circuit should be wired to the bell fault circuit using 4.5K and 2.2K resistors. This will deploy a 24 hours fault circuit.
Finally, you should perform a test by activating the output.
Menu – Engineer utilities – Test output